G. Zorer Gedik1* and A. Koyun2
1Yildiz Technical University, Architecture Faculty Istanbul /Turkiye
2Yildiz Technical University, Mechanical Engineering Fac., Istanbul /Turkiye,
Corresponding Author, gzorer@hotmail. com
In this study the experimental results of a solar energy collector which is installed to a south classroom window of a school in Istanbul are presented. The collector unit had been tested experimentally and numerical to determine its thermal performance before its integration into the south window. In this paper, the experimental analyze will be given in detail. The collector is tested using infrared radiation lamps in the laboratory. The collector reaction to change in the value of heat transfer is measured. Air temperatures and velocities are measured at the bottom (air entry) and top (air exit) of the collector. Moreover, performance of the collector geometry is analyzed using Computing Fluid Dynamics (CFD). The results of the measurements and theoretical analysis are compared. The back face of the collector is insulated to generate effective convective air flow on the basis of the test results. Then thermal efficiency measurements were executed in the classroom and the efficiency curves displayed and evaluated. A computer system with a software was designed to obtain air temperatures, velocities and solar radiation data in the classroom.
Keywords: Solar heating, solar collector, experimental, collector geometry.
A research project supported by TUBITAK (The Scientific and Technical Research Council of TUrkiye) is designed to improve the thermal efficiency of classroom design through the use of solar energy.  This paper presents a part of the results of the project. A solar energy collector was attached to a south classroom window of a school in Istanbul which has existing large classroom windows. The main components of the solar air collector are the glazing, the air space between the glazing and the collector plate, the aluminum collector profiles with air chambers and the insulated backing of the collector. (Figure 1) The function of the glazing is to admit as much solar radiation as possible and to restrict the transmission of heat radiation back through the glazing so that the optimum greenhouse effect results. Hence, the existing single glazed in front of the collector in the classroom changed the special glazing has ninety-two percent transmittance of light. 
The wavelength selective coating is applied to the front face of the collector profiles that have a low emmisivity of energy in the infrared wavelengths. Since infrared energy flow makes up a large part of the total energy loss of the system through the glazing, selective surfaces is quite effective in improving performance. 
Figure 1:The detail of solar collector. Figure 2. The profiles of solar collector.